Yes. The inputs on the SECU16Is are also configurable for supervised inputs. The only real difference is the SECU16 inputs are individually configurable, where the SECU16I is configured in banks of 8.
To auto address a single module, connect that module to the Ocelot with no other modules connected. Launch the Auto Address in C-Max. After waiting about a minute, press the Skip button until it reads the correct module number that you want the module addressed to is displayed. Press the white button on the module. The screen reading "Looking for Module #" will increment. If you have modules addressed higher than the module you are addressing, press the Skip button until the highest module number you have is displayed. Then press Abort.
ADI Tech Support